Continental Catering hoses have a yellow outer cover for the purpose of cleanliness and corrosion resistance, in accordance with BS 669 - 2:1997. In accordance with section 2.3.5 of the standard, a covered restraining device is supplied, together with the necessary mounting hardware to attach it.
They incorporate a self-sealing plug and socket.
Continental Catering hoses must be installed in accordance with BS 6173: 2001
Specification for installation of gas-fired catering appliances for use in all types of catering establishment (1st, 2nd and 3rd family gases).
Manufactured in the U.K by BS EN ISO 9001:2008 registered companies.
Under ideal conditions the following flow rates may be achieved:
Natural Gas: 1/2" Nominal Bore: up to 75,000 Btu/hour. 3/4" Nominal Bore: up to 138,000 Btu/hour.
Propane: 1/2" Nominal Bore: up to 92,000 Btu/hour. 3/4" Nominal Bore: up to 215,000 Btu/hour.
3/4" BSP Male X 3/4" BSP Female
Stainless hose and ends
Exclusive quick release brass coupler meets BS 669 Pt2
Fully welded - 100% pressure tested
Top quality PVC yellow covering - anti-wrinkle
Restraining wire included in the price
Fully approved to BS669 Part 2: 1997
Suitable for Natural Gas and LPG